Frost A5 Brochure final LR singles - Flipbook - Page 16
Floor Drains - Installation Guide
We recommend that components are
trial-assembled before installation to double
check compatibility. If used, screw the spigot
adaptor into the body outlet using a suitable
sealant to ensure a watertight joint.
2. MEASURE DISTANCE TO FINISHED
Ensure the distance between the finished
floor level and the top of pipework is
sufficient to fit the completed floor assembly.
This distance should enable the complete
assembly (with extensions, if applicable)
to be installed so that the top face of the
grating or cover finishes at the finished
If using side inlets ensure their position
allows a fall to the gully. The body must
be installed with the top of the flange at or
below membrane level.
3. INSTALL BODY
Connect body (with spigot adaptor if
applicable) to the pipework. All our bodies
can be used in solid floors.
Use a wide flanged body for timber decks.
The flange can be drilled for fixings or use
an underdeck clamp (33.9610 or 33.9620) to
fix assembly. If the deck is recessed for the
flange, consider the need to reinforce the
cut timber edge.